Question about Amana PTH123B25AJ Heat Pump Air Conditioner
Amana Heat Pump is 3 ton works okay except emergency heat will not come on...is blowing cold air.
On the heating element [behind the coil, (the springy thing)], at the top end of the element, there is a little thermistor I think it is called. You will have to remove the fan shroud. With the power off, check for continuity if you have a multimeter. If that is the problem (no continuity), you can pick one up at al local heating supply. Just have it soldered back in and reconnect. If the thermistor 's continuity is okay, remove the main board under the control knobs. I have seen these boards burn in the back where the relays are soldered on. If you're really good with a solder you can try to re-solder it. If not, it's about as cheap to buy a new unit as it is to buy the board. Good luck.
Posted on Feb 17, 2009
The problem sounds like 1 or 2 things either you have a bad sequencer for the heat strip or the emergency heat portion was not wired up.
Posted on Feb 13, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 19, 2015 | Rheem 3 Ton 14 Seer Package Heat Pump -...
Nov 26, 2013 | American Standard Heating & Cooling
Jan 31, 2011 | Goodman CKL60AR60 Air Conditioner
Jan 07, 2010 | Goodman Heating & Cooling
Jan 03, 2010 | Heating & Cooling
Oct 29, 2009 | Amana PTH123B25AJ Heat Pump Air...
Mar 29, 2009 | Goodman GMS90703BXA Heater
Dec 23, 2008 | Amana PTH123B25AJ Heat Pump Air...
Dec 15, 2008 | Amana Heating & Cooling
Dec 07, 2008 | Amana PTH123B25AJ Heat Pump Air...
Feb 02, 2016 | Amana PTH123B25AJ Heat Pump Air...
779 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: