Question about Hunter 52" Ceiling Fan With Light And Remote Control
Old fan wiring was white from fan to blue from ceiling and Red and Black from fan to white from ceiling.
New fan wiring instructions call for white from fan to white from ceiling and black and black/white wire from fan to black from ceiling.
Can you help.
People find all kinds of creative ways to wire things. White wires are always supposed to be neutrals and therefore should always go with other white wires, and colored wires should always be hot and should always go with other colored wires. If you have a voltage tester you could test to see if in fact the blue wire is actually the hot and the white is actually the neutral. (test each wire to a ground). If the previous fan was wired backwards, it would not affect the operation of the fan or lights at all. But you'd probably want to make sure the new fan was wired properly. In that case connect the white from the fan to the neutral and the black and black/white to the hot.
Posted on Jan 31, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 29, 2013 | Dryers
Sep 30, 2013 | Hampton Bay Indoor Ceiling Fans: Ceiling...
Jan 26, 2013 | Hunter Dryers
Jun 05, 2011 | Hunter 52" Ceiling Fan With Light And...
Apr 20, 2011 | Hunter (25417) Ceiling Fan
Sep 26, 2010 | Hunter Ceiling Fan Remote Receiver...
May 03, 2010 | Hunter 27187 Remote Control
Jul 14, 2009 | Hunter Ceiling Fan Light Remote Control
Mar 24, 2008 | Hunter 20531 Vista Brushed Nickel Ceiling...
Dec 26, 2007 | Hampton Bay 46175 Cameron II Plus Ceiling...
Feb 26, 2018 | Hunter 52" Ceiling Fan With Light And...
233 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: