Question about Heating & Cooling
Has 240 volts at supply point of indoor unit but will not operate using remote or temporary switch.I unplugged and removed all circuit boards around supply connection area of the indoor unit for testing before i found no Hitachi agents are in our area of Australia.
I am an old retired electrician, so are there some basic tests i can be assisted through on finding faulty board & where a replacement could be sourced?
Many thanks ...JC. Hello, I have a Hitachi RAS-25CHA indoor unit. I have purchased a PCB board from Hitachi.
I now have no idea as to fit the new PCB board. There are 2 screws on the front of the unit. I have removed these, however I am unable to remove any of the plastic head covering.
Is there a step by step procedure to replace the PCB board? Any assistance will be greatly appreciated. The heat this week is deadly!
Is the unit responding to remote instruction at all? It does sound like your board is gone. This is usually a capacitor (blue or green and round flat disc) on the pc board, and possibly one of the diodes (small black cylindrical shape with a white line on one side) Often it is the compressor drive relay (rectangular black box) on pc board. If however you have managed to find a replacement board. The plastic heads holding the pc board are released by using a small long nose pliers and pinching the bit sticking through the board. The rest is simply a matter of changing one wire at a time from old board to new board. Or a good method is just to take a snapshot with a camera to refer to regarding the wire positions.
Posted on Mar 05, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 08, 2014 | Hitachi Heating & Cooling
May 18, 2012 | Hitachi RAS-09UH Air Conditioner
Jan 15, 2011 | Hitachi Heating & Cooling
May 12, 2010 | Hitachi RAS-09UH Air Conditioner
Apr 04, 2010 | Ruud Handle Air Conditioner
Dec 18, 2009 | Hitachi Heating & Cooling
Jan 08, 2009 | Hitachi RAS-09UH Air Conditioner
Jul 21, 2008 | Hitachi Heating & Cooling
156 people viewed this question
Usually answered in minutes!