Question about Air Conditioners
Two of the 4 thermostats in our house (for water circulating radiant heat) have on occasion had blank screens for several hours, then spontaneously came back on. Turning them off and on or changing the temperature had no effect. Is this a known problem> Should they be replaced?
I have the same problem. It's because your domestic hot water (dhw) is on the same system as your radiant heat. In these systems, dhw is given priority over floor heating. That is, when your dhw needs heat, power to your Tstats are shut off until your dhw is satisfied. (Makes sense: cold showers no fun) Your T8400B's have no battery, so they are dead unitl power to them is restored by your zone control. It's really stupid that they use these Tstats, because you can't even SEE your room temp or settings let alone change them. I will be replacing my Tstats with battery powered soon; hopefully that will allow me to see and adjust during dhw cycles.
Posted on Nov 07, 2009
Most likely a bad tstat i would replace I recommend honeywell focus pro 6000
Posted on Aug 29, 2009
Tips for a great answer:
Sep 11, 2015 | Honeywell CT31A - Economy Heat/Cool...
Nov 29, 2013 | Air Conditioners
May 14, 2013 | Honeywell Rth2310b 5-2 Day Programmable...
Jul 04, 2011 | Air Conditioners
Apr 26, 2011 | Honeywell Air Conditioners
Dec 05, 2010 | Honeywell Air Conditioners
Jun 21, 2009 | Honeywell Air Conditioners
May 10, 2009 | Air Conditioners
Dec 31, 2008 | Honeywell Air Conditioners
May 27, 2008 | Honeywell Air Conditioners
502 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: