Question about Air Conditioners
Try to replace the compressor start capacitor, located on the outdoor unit, remove top cover. Check mfd rating and replace with same.
Posted on Mar 12, 2009
Tips for a great answer:
Jan 25, 2015 | LG Air Conditioners
Nov 09, 2013 | Ruud UBHC Air Conditioner
Apr 16, 2012 | Air Conditioners
Feb 05, 2011 | Cfm Daikin R410a Split System Air...
Sounds like you have and open limit switch trace the wires from the gas valve one will go straight to the terminal board the other one will go through all the safety limits take an ohm meter (an ohm meter beeps or lights up when you touch the leads together showing a direct connection also called continuity) and check each limit switch by touching one of the meters leads to one wire on the switch and the other meters lead to the other wire on the switch if no continuity is there your switch is open some switch's have little reset buttons on them. Find the open switch and reset or replace.
Nov 25, 2010 | Air Conditioners
Oct 03, 2010 | Air Conditioners
May 31, 2010 | Air Conditioners
Jan 04, 2010 | Amana Comfort Zone 12M32PBEH Air...
14 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: