Question about Heating & Cooling
Try to replace the compressor start capacitor, located on the outdoor unit, remove top cover. Check mfd rating and replace with same.
Posted on Mar 12, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 25, 2015 | LG Heating & Cooling
Nov 09, 2013 | Ruud UBHC Air Conditioner
Apr 16, 2012 | Heating & Cooling
Feb 05, 2011 | Cfm Daikin R410a Split System Air...
Sounds like you have and open limit switch trace the wires from the gas valve one will go straight to the terminal board the other one will go through all the safety limits take an ohm meter (an ohm meter beeps or lights up when you touch the leads together showing a direct connection also called continuity) and check each limit switch by touching one of the meters leads to one wire on the switch and the other meters lead to the other wire on the switch if no continuity is there your switch is open some switch's have little reset buttons on them. Find the open switch and reset or replace.
Nov 25, 2010 | Heating & Cooling
Oct 03, 2010 | Heating & Cooling
May 31, 2010 | Heating & Cooling
Jan 04, 2010 | Amana Comfort Zone 12M32PBEH Air...
14 people viewed this question
Usually answered in minutes!