Question about Ruud UAMB Air Conditioner
I have lost the wiring diagram for this unit and would like a new one if possible.
The wiring on these is pretty straight forward
Basically a contactor, either DPST or DPDT, depending. Input power connects here.
Compressor C terminal connects to one side. R terminal connects to the other. 1 terminal of the run capacitor connects to the terminal with the R terminal of compressor. The other side of run capacitor hooks to S terminal of compressor. One wire of condensor fan hooks with compressor R terminal, the other condensor fan lead hooks with compressor C terminal.
Only things missing from all this is a hard start kit and crankcase heater. Let me know if you want to know how to hook those up.
Posted on Jan 29, 2009
Tips for a great answer:
Aug 18, 2010 | Ruud UBHC Air Conditioner
Jun 28, 2010 | Ruud UBHC Air Conditioner
May 27, 2010 | Air Conditioners
May 23, 2010 | Ruud Matching Split Air Conditioner
Apr 06, 2010 | Ruud UPMC036 Air Conditioner
Jun 26, 2008 | Air Conditioners
Jan 05, 2008 | Air Conditioners
Nov 24, 2007 | Ruud UBHC Air Conditioner
Aug 08, 2013 | Ruud UAMB Air Conditioner
576 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: