Question about Aprilaire 700 Humidifier
Climbs above 25%. How do I fix the problem???
Have you measured the amount of water dripping into the drain? The specification is 1 quart in 2 and half minutes. If it is much less, get your solenoid checked. I had the same problem and got it replaced and it works as per specification now. You also need to see how many minutes in an hour your furnace is actually running. The humidifier runs only when the furnace is, so the more it runs the better. The specification is 35% with the furnace running at 70%.
Posted on Jan 31, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 04, 2015 | Humidifiers
Feb 23, 2011 | Honeywell HE360A1027 Whole House...
Jan 25, 2011 | Honeywell HE365 Humidifier
Jan 20, 2011 | Aprilaire 400 Humidifier
Dec 28, 2010 | Aprilaire 700 Humidifier
Mar 03, 2010 | Aprilaire 700 Humidifier
Mar 03, 2010 | Aprilaire 600 Humidifier
Nov 28, 2009 | Aprilaire 600 Humidifier
Jan 15, 2009 | Kenmore Humidifiers
Mar 06, 2007 | Aprilaire 600 Humidifier
134 people viewed this question
Usually answered in minutes!