Question about Goodman GMS90703BXA Heater
When I tun the heater on, there is a delay before it starts firing up the heat & fan part, then it shuts off and restarts over and over again.
There is a little rod that sits in front of one of the flames called a flame sensor/detector, after a few years corrosion can build up on it. There is a little screw you take out then removed the rod, clean it with sandpaper (very fine) and then put it back. If corrosion is built up on this, it cannot detect the flame..this was my problem and it was easily fixable.
Posted on Feb 24, 2009
Sounds like a dirty flame censor to me
Posted on Feb 24, 2009
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remain solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the ignitor. The ignitor will glow and you will be able to see it if viewed thru the small inspection port. Once the ignitor gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the ignitor does not energize (bad control, bad ignitor), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not lite (dirty pilot), the burner does not lite (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Most newer furnaces will have a diagnostic center or control built into the control module. You may be able to view it as it is running thru a small viewing port. Some models will require the removal of an access panel prior to finding it. On the reverse of the access panel, there will be a diagnostic chart that will aide you in understanding any error code recorded (usually a blinking light).
Posted on Feb 18, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 07, 2015 | Pool & Spa
Jan 06, 2014 | Coleman Home Electric Furnace Eb15b/Eb15d
Aug 05, 2017 | Williams 3003622 Ceramic Wall Mounted...
Apr 21, 2017 | Heating & Cooling
May 09, 2010 | Noritz 6.3 Gallon Residential Tankless...
Jun 26, 2009 | Pentair Minimax NT Heater
Jun 07, 2009 | Hayward H Series Pool & Spa Heater 400k...
May 26, 2009 | Heating & Cooling
Feb 28, 2008 | Vacuums
Dec 30, 2007 | Heating & Cooling
198 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: