Question about Goodman GMS90703BXA Heater
The unit will go through a heat cycle but the combustion and circulating fans will not shut off, it has had two new boards put in it and is still doing the same thing. Every component in it checks out as good but the fans will stilll not shut off.
It sounds like it is still receiving a "call" for heat from the thermostat. First check that the thermostat is set for gas heat and not electric.(There may be a jumper or dip switch on the back). Read the directions with the thermostat.
Secondly, Verify that the wiring at the thermostat is correct. (R- to red, W to white, G to green etc.)
Third, If the first two do not fix the problem, then there is definitely a problem in the thermostat wire between the furnace and the thermostat. (usually the "R" and "W" wires will be crossed or shorted to the sheet metal around the furnace. You may just have to replace the entire wire. Best of luck!
Posted on Jan 29, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 17, 2014 | Heating & Cooling
Nov 02, 2010 | Goodman Heating & Cooling
Apr 23, 2009 | Intertherm P3RA-048K Air Conditioner
Feb 03, 2009 | Heating & Cooling
Feb 03, 2009 | Goodman GMS90703BXA Heater
Feb 03, 2009 | Goodman CLQ36AR49 Air Conditioner
Jan 29, 2009 | Heating & Cooling
Jan 27, 2009 | Goodman CLQ36AR49 Air Conditioner
Nov 18, 2008 | Goodman GMS90703BXA Heater
Sep 21, 2008 | Goodman Heating & Cooling
110 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: