Question about Williams Heating & Cooling
15 year old Willams 3508331 makes an increasingly loud puff or mini-explosion when finishing a heating cycle (when main flame goes out).
I don't think it is dangerous yet, but would like to know the cause.
Williams, LP provider and place I bought it only say to clean it, so I have removed the whole burner assembly and blown out with compressed air a twice with no effect.
Any ideas would be appreciated
And one last thought I forgot to put in the previous that you reminded me of -
LP or propane fired units do tend to backfire when they go out. Has to do with the residual gas pressure after the valve closes. My only suggestion is to have the gas pressure measured and the regulator at the tank adjusted. I believe it should be 9.5" -11.00" W.C (water column) but I would have to pull a book to remember for sure. Proper pressure will assure minimal backfire.
Posted on Jan 29, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
May 09, 2011 | Rheem Tankless Hot Water Heater...
Jan 18, 2011 | Heating & Cooling
Apr 25, 2010 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Feb 26, 2010 | Heating & Cooling
Jan 02, 2010 | Reddy Heater-30-55,000 BTU Variable
Oct 23, 2009 | Dayton Gas Fired Heater LP TC200VA - Heats...
Feb 05, 2009 | Reddy Heater-170,000 BTU Kerosene Deluxe
Jan 03, 2008 | Goodman GMS90703BXA Heater
Dec 29, 2007 | Williams 2509612 Ceramic Mid-Size Heater
318 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: