Question about Goodman Heating & Cooling
Unit about one year old. The unit trips a 20 amp breaker every once in awhile. Cause unknown. Company noted 78 amps once when starting. Company who installed the unit place a hard start kit on th unit. The unit is mounted about 15 feet from inside unit. Inside unit down flow GR28K7-PFV-270.
20 AMP Circuit, huh? More on this below.
The tech probably didn't put a hard start kit on, but if he did, I hope he added the resistor to the start capacitor, or you could have a problem in the future. He probably put a soft start on it, a 2 wire device which looks like a capacitor. But only you will know for sure (or he.). As for warranty, manufacturers don't care about soft or hard start kits. In fact, they like 'em, because they extend the life of the compressor, which keeps them from having to pay for a new one.
I would be concerned with a 20 AMP circuit for anything higher than 2 tons. Take a look at the nameplate rating on the side of the condensor and tell me how many Running Load Amps (RLA) this unit is supposed to pull.
Also need to know your line voltage at the condensor, with the unit running.
Posted on Jan 28, 2009
Short cycling of the compressor can be an inconsistent cause of a breaker overload. It happens when the compressor start winding is "jolted" into operation several times over a short period this can happen when there is a loose power or control wire connection that is broken from the vibration at start up of the compressor or by the occasional "jiggling" of the mercury in older analog thermostats. I suggest that all electrical connections are checked and that you use a newer model thermostat, if its not already that has a built in start delay circuit.
Hope this helps you if your still having trouble with this issue.
Posted on Jan 28, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 25, 2015 | Hobart C44a Commercial Dishwasher
Jul 28, 2013 | Frigidaire FAD504TDD Dehumidifier
Jul 18, 2011 | Heating & Cooling
Sep 30, 2010 | Carrier 38CKC036 Air Conditioner
Aug 19, 2010 | Sub-Zero 690 Side by Side Refrigerator
Jul 03, 2010 | Goldstar M1003R Air Conditioner
Apr 11, 2010 | Danby DMW112 Microwave Oven
Jun 15, 2009 | Heating & Cooling
Mar 22, 2009 | Rule H53sp 24mgra Swimming Pool Cover Pump...
Sep 03, 2007 | Heating & Cooling
451 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: