Question about LG LMU366HV Air Conditioner
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
CH-06 REFERS Indoor unit coil sensor fault. Disconnect from PCB measure resistance. 10 kOhm at 10C and 4 kOhm at 30C. if not replace sensor. THANKS.
Posted on Dec 13, 2010
SOURCE: Our LG Art cool Airconditioner
Inverter compressor run current high. Check compressor windings all equal 1 to 4 OhmsCheck to earth 50 MOhm minimum, check run current. If high, winding is weak. Solution: Replace compressor.
Posted on Jan 20, 2011
SOURCE: I have a new LG
Reverse or open phase. Check all 3 phases are present and correct. If correct voltage appears at all three phases, swap any two to cure the fault. Thanks. Helpful?
Posted on Feb 12, 2011
Tips for a great answer:
Oct 15, 2016 | LG Art Cool LA181CNW Split System Air...
Sep 01, 2015 | LG Heating & Cooling
Mar 15, 2015 | LG Washing Machines
Apr 16, 2012 | LG Dehumidifiers
Jun 16, 2011 | Heating & Cooling
Dec 13, 2010 | LG Art Cool LA121HNP Split System Air...
Mar 02, 2009 | Heating & Cooling
103 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: