Question about Ducane 30400042 (LP)
Furnace is running nornal this last hour.
1 do you have a program or mercury buld mercury bulb.is usally a adjustable heat anticipator which a digital is fixed I recommend a digital t stat but also be advised that mercury bulb tstat are really phased out you could also have a issue with your main limit inbetween the heat exchanger wheather it is a cam stat or a normally closed limit but being a new furnace its more likely to be a n/closed limit will open if there is to much heat in supply box above the evap coil.you would need to take your delta temp reading within manufacture specs..or call aca or your local hvac company 770 932 8990 ask for mr.blaine to schedule your appointment today or are office staff thanx.
Posted on Jan 24, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
A short cycle heat cycle indicat a pressure switch replacement was needed. This did not fix the problem. the problem was in PCV line since the end was filled with slugs and cause the line to backup with water. When this happen the system would stop asking for gas. the water would leak out and it would restart. The problem was fixed by cleaning value at end of PCV. This released the water, two quart of water, that was back up causing problem. Curious if a filter change indicator was providing a clue that was missed?
Posted on Feb 24, 2009
Tips for a great answer:
Jan 09, 2015 | Emerson Lennox Ducane Armstrong Furnace...
Feb 13, 2013 | Honeywell Furnace Gas Valve Sv9501h2409
Dec 17, 2012 | Honeywell Furnace Air Pressure Switch...
Feb 24, 2011 | Dayton Gas Furnace Heater
Feb 24, 2011 | Heating & Cooling
Dec 05, 2010 | Heating & Cooling
Jan 28, 2009 | Ducane 436 inch 2 - 2 burner Grill
Jan 15, 2009 | Heating & Cooling
Nov 15, 2008 | Kitchen Appliances - Others
82 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: