Question about LG Heating & Cooling
Air conditioner screen switched off and showed -Water level float switch error. We reset the airconditioner and it is now running.
What does this fault mean, and where is the float switch on reverse cycle LG air conditioner
You do not mention the model, I presume that it is a cassette, in which case the float switch is located in the indoor unit. You have to remove the cover which is 4 screws. First make sure all power supply is turned off. Then remove the drain pan which surrounds the fan blade. You will see in one corner of the unit a slightly deeper part of the drainpan, this is the corner where both the condensate pump as well as float switch is located. Before you do any of this, give a serious blow into the drain pipe from outside and this may dislodge any sludge which may be causing the floatswitch to stick. You can also pull out a rubber plug which is under the pump on the drainpan.
Posted on Mar 05, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 26, 2014 | LG LMN127HVT LMN127HVT 12 000 BTU Ductless...
Jan 11, 2011 | Haier Heating & Cooling
Jun 07, 2010 | Frigidaire FAP094P1Z Portable Air...
May 20, 2010 | Danby Portable Air Conditioner
Nov 22, 2009 | Panasonic CW-XC243HU Air Conditioner
Jun 29, 2009 | Sunpentown WA-1210E Air Conditioner
Jul 27, 2008 | Sharp AF-S100FX Air Conditioner
Feb 11, 2008 | Mitsubishi MS12TN Air Conditioner
1,124 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: