Question about Heating & Cooling
Pilot light won't stay on on the boiler side of the rayburn - have pressed reset button - pilot lights, then immediately goes out, then comes on. then goes out and so on......
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The pilot flame must touch (burn) the tip oqef the t-couple to hold the magnet in the gas value open.make sure the pilot orifice (hole) is clear.the pilot pressure (in the tube) is factory set full open & can only be adjusted down (less). Also check the gas **** didn't get closed or turned half way.? Assuming its not the t-couple. If all is good & it still won't stay on. Replace the gas value.!
Posted on Sep 21, 2011
SOURCE: Pilot light won't ignite
Wait 30 minutes; press reset button. Repeat if necessary.
4. Pilot light out. 4. Relight pilot. 5. No gas. 5. Make sure
gas valve to furnace is fully open. Not enough ...
Just checked this site. I am sure you will find it useful - Good luck
Posted on Feb 07, 2012
try cleaning the pilot light jet, usually gets dust etc inside it. clean it with a pin. but remember do not mess with gas appliances if you are not confident enough. as being cold will be the least of your worries lol
Posted on Feb 16, 2012
Testimonial: "Thank you, i will give that a try..."
Tips for a great answer:
Dec 23, 2013 | Heating & Cooling
May 26, 2012 | Water Heaters
Feb 07, 2012 | Heating & Cooling
Sep 20, 2011 | Heating & Cooling
Apr 23, 2010 | Heating & Cooling
Oct 25, 2008 | Water Heaters
Oct 22, 2008 | Honeywell Heating & Cooling
Apr 21, 2018 | LG Heating & Cooling
257 people viewed this question
Usually answered in minutes!