Question about Goodman Manufacturing GPG1342090M41 Packaged Furnace/Air Conditioner, Gas/Electric - 13 SEE
If I take cover off t-stat then put it back on unit fires
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 22, 2015 | Goodman Heating & Cooling
Jan 01, 2015 | Goodman Manufacturing Goodman GPH1348M41 4...
"PLACE A JUMPER (PIECE OF WIRE) BETWEEN Y AND W IF YOU ARE USING A HEAT PUMP WITHOUT AUXILIARY/BACKUP HEAT." if this dosnt work check the fuse in the air handler you may have blown it if you did not turn the unit off before installing.
Mar 25, 2014 | Goodman Heating & Cooling
Nov 29, 2013 | Goodman Manufacturing Goodman GPH1530M41...
Aug 17, 2012 | Goodman Heating & Cooling
Mar 02, 2011 | Amana Heating & Cooling
Dec 24, 2009 | Goodman CKL24AR24 Air Conditioner
Oct 21, 2008 | Goodman CLQ36AR49 Air Conditioner
Oct 09, 2008 | Goodman Heating & Cooling
109 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: