Question about Heating & Cooling
Check the blower motor capicator. It should be mounted close to the motor with 2 wires to it (brown,brown/white).
Turn the blower on the thermostat and spin the squirrel cage by hand and see if it runs after by itself. If it does then definitely the capicator is bad .If it still doesn't run then check to see if there is voltage going to motor.
If thermostat is calling for fan and there is voltage present at the motor terminal then the motor is bad
Posted on Jun 01, 2017
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
On the heating element [behind the coil, (the springy thing)], at the top end of the element, there is a little thermistor I think it is called. You will have to remove the fan shroud. With the power off, check for continuity if you have a multimeter. If that is the problem (no continuity), you can pick one up at al local heating supply. Just have it soldered back in and reconnect. If the thermistor 's continuity is okay, remove the main board under the control knobs. I have seen these boards burn in the back where the relays are soldered on. If you're really good with a solder you can try to re-solder it. If not, it's about as cheap to buy a new unit as it is to buy the board. Good luck.
Posted on Feb 17, 2009
Tips for a great answer:
Jan 11, 2011 | Amana PTH123B25AJ Heat Pump Air...
Oct 22, 2009 | Amana Heating & Cooling
Jan 30, 2009 | Amana PTH123B25AJ Heat Pump Air...
Jan 20, 2009 | Amana PTH123B25AJ Heat Pump Air...
Dec 07, 2008 | Amana PTH123B25AJ Heat Pump Air...
49 people viewed this question
Usually answered in minutes!