Question about Utilitech 3/4-HP 15 GPM Shallow Well Jet Pump 3/4-JET
I have a 3000 gallon water tank outside filled up.,and it is hosed underground into the basement.from there it is connected to,the pump..all was fine and well,until this afternoon..the pump keeps running,and no water is being pumped.,but with the pump off I have good pressure..it runs throughout the Ouse..,but my up p isn't pumping it anymore,I don't know why..it is the Impeller..gone bad??...Thaks."
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Good you got it working. Please post again if you have more trouble on this or another item. Also be sure and check what I mentioned just in case you are operating at the margins, don't want a failure right after you got it going!
Posted on Sep 16, 2012
SOURCE: I have a utilitech convertable pump. It is used as a shallow well pump at the moment. It worked fine untill last week, the hot water tank went bad and we replaced the tank and all the above ground li
Your problem is that your "water bound"...
Your water tank must have a cushion of air for the pressure switch to work properly.
Turn off your pump and drain about 1/3 of the water from your tank.
Once you have an "air cushion" the pump and switch will work properly.
You can also add air pressure using an air compressor and an air valve installed on the top of your water tank or maybe on the side or bottom of the tank.
You would put air into the tank until about 1/3 of the water is gone replaced with the air.
Once that is complete your problem will be solved.
Please take time to rate me
Posted on Oct 25, 2012
Tips for a great answer:
Nov 17, 2015 | Jet Plumbing
Nov 29, 2014 | Utilitech 1/2-HP 9-GPM Shallow Well Jet...
Jun 27, 2014 | Utilitech 1-HP Cast Iron Shallow Well Jet...
Apr 12, 2014 | Wayne WATER SYSTEMS SWS50-12P 1/2 HP...
Oct 20, 2012 | Plumbing
Sep 15, 2012 | Utilitech 1-HP Cast Iron Shallow Well Jet...
Feb 12, 2011 | Flotec Corrosion Resistant Shallow Well...
Sep 24, 2009 | Flotec Corrosion Resistant Shallow Well...
Aug 30, 2009 | ACE JET PUMP For shallow well
May 05, 2009 | Flotec Corrosion Resistant Shallow Well...
61 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: