Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You need to remove the flame sensor on the far left hand of the burner. In has a single wire going to it in between the jets. I believe it is a white wire. A 1/4" screw holds it in place. It has a white ceramic base with a stainless steel looking probe that protrudes into the flame of the burners. Pull the wire off of it, then remove the flame sensor from the burner assembly.. Use steel wool to clean the metal probe until shiny. Re-install and enjoy your heat.
Posted on Oct 07, 2009
Yes, inspect the air intake, exhaust pipe, filter and condensate piping for blockage or moisture. Also check for a hole in the hose that goes from the small exhaust blower to the pressure switch or a bad connection on the switch or control board. You may be able to temporalily jump the switch for diagnostic purposes only.
Posted on Oct 17, 2009
for what ever reason, your shutting down on high temp
4 things to check
1 the filter
2. your fan, is it comming on....... to circulate the heat.
3. your hi temp thermostat is bad and needs to be replaced.... it should be a sqaure with two wires
you can just ohm it out to know sometimes orange but it differs some
4. above your fan are the coils, ar5e they clean and free of restriction
Posted on Oct 28, 2009
The unit is not sensing a flame. A flame sensor is a piece of metal rod about 1/8" in diameter which tells the unit it is burning. take it off and clean it with steel wool. if that doesn't work you'll need to replace it
Posted on Nov 03, 2009
Tips for a great answer:
Mar 02, 2015 | Heating & Cooling
Feb 03, 2015 | Heating & Cooling
Feb 04, 2014 | Heating & Cooling
Dec 05, 2013 | Heating & Cooling
Mar 01, 2013 | Heating & Cooling
Nov 12, 2012 | Heating & Cooling
Mar 15, 2011 | Ruud Heating & Cooling
Dec 14, 2008 | Cross Furnace Draft Inducer Blower 115...
Dec 08, 2008 | Water Heaters
17 people viewed this question
Usually answered in minutes!