Question about Goodman GMS90703BXA Heater
Elliselect,Thanks for the information about wind chill effect! Look on the circuit board for a set of dip switches(Usually a small red block containing white switches about 3/8 of an inch long) or a jumper. (The jumper looks like the one you commonly find on the back of a hard drive). Either one is usually clearly marked on the board in numbers representing seconds of time. You can set the blower OFF delay for any one of these options. For more complete instructions please read your user manual. If you do not have a manual you might be able to find one on the goodman.mfg.com website. Best of luck!
Posted on Feb 03, 2009
Could be that the fan on you new furnace is more powerful than your old one and is forcefully blowing the cold duct air out causing a temporary chill or it could be that you need to adjust the fan delay.
I'm not familar with this unit so I wouldn't have aclue on how to do this or even if you can.
Posted on Jan 29, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 10, 2016 | Goodman Heating & Cooling
Jun 27, 2008 | Goodman Heating & Cooling
Feb 27, 2014 | Goodman Manufacturing Goodman...
Jan 28, 2014 | Goodman Manufacturing Goodman 60,000 btu...
Oct 06, 2012 | Cozy Enclosed Front Console Heater 70,000...
Oct 06, 2012 | Goodman Manufacturing GMH950453BX - 45,000...
Oct 29, 2010 | Goodman GMS90703BXA Heater
May 14, 2010 | Goodman GMS90703BXA Heater
Mar 24, 2010 | Goodman GMS90703BXA Heater
Nov 07, 2008 | Goodman GMS90703BXA Heater
385 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: