Question about Jandy Lite 2 Natural Gas Pilot Light Heater
Jondi lj400p eletric
The FL2 code indicates that the heater has tried and failed to ignite three times. This is not uncommon after it has sat for a while unused. Check that the gas shut off valve is open and the valve inside the heater is in the on position. While it is trying to fire check to see if the hot surface igniter glows, then you should hear an audible "clunk" that is the pilot valve opening. If the pilot valve is opening but the HSI is not glowing then the HSI will need to be replaced. This is not uncommon.
To clear the FL2 service code, turn off the heater by using the SELECT key to turn the heater to the 'OFF' position and then turn it back to either 'POOL' or 'SPA'. The heater will now go back to the normal operating mode. If there is a call for heat the heater will attempt ignition again. If the ignition fails
again, contact a qualified technician to check the heater.
Posted on Jan 29, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 20, 2014 | Jandy Lite2 LJ 400P, 400,000 BTU Heater,...
Feb 17, 2011 | Jandy Laars Lite2 Lj 250,000 Btu Heater
May 31, 2010 | Jandy Lite 2 Natural Gas Pilot Light...
May 27, 2010 | Jandy Lite 2 Natural Gas Pilot Light...
Apr 01, 2010 | Jandy Lite 2 Natural Gas Pilot Light...
Aug 02, 2009 | Jandy Lite 2 Natural Gas Pilot Light...
Jun 07, 2009 | Jandy Lite 2 Natural Gas Pilot Light...
Sep 25, 2012 | Jandy Lite 2 Natural Gas Pilot Light...
1,176 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: