Can somebody help,why is my Central AC blows
Most heat pumps have an auxillary heat. Many are electric auxillary heat with a heat strip in the air handler. A common malfunction is for the electric auxillary heat to operate when the heat pump is set on cool. To confirm this, locate the conductor that runs from the heat sequencer to the connection on the heat strip. You will see this on the top section of the air handler. Use the clamp on part of the amp meter over that wire. If the thermostat is set on cool and the heat strip is drawing amps, it means the heat is coming on while the heat pump is set on cool. There is usually one or two causes for this, either the sequencer is bad or there is low voltage wires usually behind the thermostat or in the air handler closet that are touching that shouldn't be touching.
If this is not the case, if its not a problem of where the heat is coming on with the air conditioner, it could be a case of the reversing valve malfunctioning. The way a heat pump works is it reverses the flow of the refridgerant. For instance, many heat pumps the reversing valve is activated in cool. That would mean that there is a low voltage circuit that activates the reversing valve when the heat pump is in cool. I'm not sure what model/brand your heat pump is, Goodman and Janitrol for instance, the heat pump reversing valve is activated in cool. In any case, if the reversing valve is not operating properly, when the air conditioning is set to cool it will actually be heating. Or you could set it to heat and it may actually be cooling instead of heating. Please check these two items first and if you have any further questions, please let me know. Especially if you know of any additional problems like the evaporater is icing up or if the air handler fan is not operating when it should.
Aug 31, 2009 |
Heating & Cooling