Question about Heating & Cooling
House was built in 2004 and we just have heat only no ac
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Honeywell Gas Furnace
A Make and Model number of the furnace not the thermostat will help but I can walk you thru the operation of a typical furnace. It sounds to me that the burners are igniting properly but the flame sensor is not sensing the flame and shutting down the system. You will need to find the sensor and clean it and check the wire from it to the control board. Typically, the flame sensor is found at one side or the other of the burner box. It is a small probe that the flame hits. Depending upon your model it may have a small wire attached to it leading back to the control. Or it may be part of your auto-pilot assembly. ? At any rate, you will need to get to it and very delicately brush it off. Then inspect the flame channel. This is a trough area where the flame travels to ignite all burners. Over time, they tend to fill with rust and debris. Take a small screwdriver and run the blade down the trough. Inspect the wire that goes from the flame sensor to the control board. Make sure it is not frayed or broken or shorting out and that the connection at the board is good.
Beyond that, it's time for a technician to come.
Let us know the Make and Model of the furnace (found inside the furnace cabinet) and maybe we can help you further.
Posted on Nov 20, 2007
Try cleaning the flame sensor. It is located right besides the last burner. Looks like a thick piece of wire. Take steel wool and gently remove the carbon that has built up. Should only take 4 or 5 strokes. Let me know how it goes after that. ken
Posted on Dec 23, 2008
Look at the contactor on the condensing unit, remove the low voltage wires to the contactor and turn on the system. If the low voltage fuse doesn't blow, replace the contactor.
Posted on Jul 07, 2009
Make sure filters are clean . if they are stopped up the unit will over heat. Lets start there. Russ
Posted on Mar 23, 2010
Testimonial: "James, YOU DA MAN!! I would have never guessed the filters could cause these symptoms. Recent carpet cleaning may have added to filter clogs."
Tips for a great answer:
Nov 20, 2016 | Heating & Cooling
Jan 05, 2016 | Heating & Cooling
Oct 27, 2010 | Amana Heating & Cooling
Mar 24, 2010 | Goodman GMS90703BXA Heater
Jul 03, 2009 | Heating & Cooling
Jan 17, 2009 | Weather King 10AJA3601AH Air Conditioner
Jan 13, 2009 | Heating & Cooling
Dec 23, 2008 | Heating & Cooling
May 21, 2008 | Heating & Cooling
13 people viewed this question
Usually answered in minutes!