Question about Leviton 1755 Triple Rocker Switch Decora
I am replacing an older Beoan unit that had heat, fan & light. When I wired the new one have only heat with no light or fan.
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The switch that you have works like 3 seperate switches. most of these switches will have gold screws
on one side and silver screws on the other side, lets say that the left is gold and the right is silver, and
the switch may also have a green screw for ground. your 12/2 with ground is your main hot, you may
want to mark it with a piece of tape, so you know it's the incoming hot. the ground off your hot will tie,
to the green screw on switch and continue and tie to your vent light which should also have a ground
the white coming off the hot is your neutral, it will go straight to your white or whites on your heater.
the black hot wire at your switch will go to each gold terminal on one side of the switch,there are two
ways you can do this, go to one side and just run a jumper, or put one wire on each gold screw and
tie in to your hot-black wire with a wire nut. now for the switch legs, you will need to run from your, switch
to your heater either another pair of 12/2s or a 12/3, each side of the switch that has one silver screw,
it's easier with a 12/3 normally a 12/3 will have a red,black,white,and ground.
top switch red to red on heater,black to black on light and the white blue on the vent,so from your switch
to the heater you would have to run a12/2 you would not use the black only the white and ground.
remember the white-neutral coming from the switch will be tied to all the whites at the vent,light,heater
except for the 10/3. the 10/3 is used stricktly for the switch legs. good luck!
Posted on Jul 10, 2011
Tips for a great answer:
Dec 26, 2015 | Dryers
Oct 20, 2013 | Broan NuTone 100HL Combination Bathroom...
Jul 09, 2011 | Leviton 1755 Triple Rocker Switch Decora
Aug 12, 2010 | Broan-NuTone Dryers
Jul 12, 2010 | Broan-NuTone N-763RLN Combination Light...
Mar 29, 2010 | Broan-NuTone Heating & Cooling
Dec 27, 2009 | Broan-NuTone N-9093CH Combination Heater...
Oct 09, 2009 | Dryers
Sep 02, 2009 | Heating & Cooling
Aug 28, 2009 | Broan-NuTone (8663RP) Ceiling Fan
67 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: