Question about Heating & Cooling
Air filter for Goodman heatpump Model #ARIF182416CA SERIAL #1201162219
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
On your t-stat you have Y, W1, W2, R, O, G, B or C or X. Y is your cooling circuit and will be the same in the air handler and heat pump unit, use the yellow wire for this circuit. W1 and W2 are your back up elec. or gas heat. Depending on how many kws or heat strips you have and t-stat wires you will put the white wire to W1 in both the t-stat and air handler. W2 is for your second stage back up heat if air handler calls for it, this will be a tan or brown or black t-stat wire and goes to W2 on t-stat and air handler. R is half of your 24v control power from the transformer and is the red wire and goes to the t-stat, air handler, and heat pump. O is for the reversing valve in the heat pump that switches it from heating and cooling. You guessed it the orange wire connect to t-stat and heat pump. G is for the blower and is the green wire to the t-stat and air handler. B or C or X is known as the common which is the other half of control circuit from 24v transform it is the blue wire and goes to the t-stat, air handler, and heat pump.
Posted on Oct 09, 2008
The condenser fan motor has gone bad... this is a very common problem. Find the specs. on the side of the motor and then get a replacement from Goodman or from a company like www.grainger.com
The fan motor is rather easy to replace, the worst part is getting the fan blades off of the shaft of the old motor. Use WD-40 and be patient...
Posted on Apr 07, 2010
Tips for a great answer:
Aug 23, 2014 | Goodman Heating & Cooling
Mar 27, 2014 | Goodman Heating & Cooling
Jan 03, 2011 | Goodman CLQ36AR49 Air Conditioner
Aug 29, 2010 | Goodman Heating & Cooling
Aug 05, 2010 | Goodman CKL36AR36 Air Conditioner
Jun 09, 2010 | Goodman GPC1342H21A Air Conditioner
May 19, 2009 | Goodman CLQ36AR49 Air Conditioner
Sep 15, 2008 | Goodman Heating & Cooling
284 people viewed this question
Usually answered in minutes!