Question about Aprilaire 600 Humidifier
Power humidifier warm air side installation
humidifier does not come on when second stage heat does. Fan on the humidifier comes on but the water is not supplied to the unit. It does come on with fan and water during the 1st stage.
If the installer used a #50 relay when they installed it they did not take in consideration the the fan will run at two different speeds in heating. Remove the #50 relay from the blower wire it is connected to. Reinstall it on the blowers white wire (neutral). This should fix the problem.
Posted on Mar 29, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 26, 2015 | Honeywell HE120 Humidifier
Unless you are using a current sensing relay or sail switch, you need to get the humidifier power from the blower motor supply so it only operates when the blower is on.
Since you can manually control the humidifier, there is not a fault with the solonoid.
Oct 19, 2007 | Honeywell HE360A1027 Whole House...
Mar 17, 2011 | General Filters 1042-LH Humidifier
Mar 10, 2010 | Aprilaire Humidifiers
Mar 05, 2010 | Honeywell Power Humidifier: Furnace...
Mar 03, 2010 | Aprilaire 600 Humidifier
Jan 26, 2009 | Humidifiers
Jan 17, 2009 | Honeywell HE220A1019 Whole House...
May 22, 2017 | Aprilaire 600 Humidifier
132 people viewed this question
Usually answered in minutes!