Question about Specialty Electrics
We have a 2 story house with 2258 sq. feet. There are laminate floors in the entire downstairs and carpet upstairs. We have 1 honeywell thermostate that is located in the hallway of the upstairs. The vents downstairs blow cool air? If you come from outside, it does feel fairly warm on the main level but when you go upstairs, it is much warmer.
Some of this depends on where the air handler/furnace is located. Most often in two story houses, it's in the attic upstairs, or in a closet upstairs. A duct routes air from the furnace to the downstairs supply duct, so it is a distance from the air handler.
When the unit first initiates a heating cycle, that duct is going to be full of cool air, and the duct itself will be cool. So the furnace has to run long enough to push the cool air out, as well as warm the duct up, before your going to feel warm air at the registers downstairs.
Keep in mind, heat rises. And, your thermostat only monitors the immediate area where it's located. In your case, upstairs.
Two story houses are problematic because of this. And one way around it is to have a damper system installed that distributes the air upstairs or downstairs based on a thermostat located in those spaces. There would be 2 dampers, and 2 thermostats (one upstairs, one downstairs). Each stat would control a damper, and the call for heat or cooling.
Let me know if you would like to consider a system like this, and I can point you to components to use. I've put several system like this in.
Posted on Jan 27, 2009
Tips for a great answer:
on Dec 18, 2009 | Specialty Electrics
Mar 26, 2012 | Specialty Electrics
The Home-tek steam mop is designed for
use on tile, vinyl and wood laminate flooring. This type of mop works a
bit differently than your regular cleaning mop, as it uses steam to
safely sanitize your hard flooring surfaces while removing stuck-on
Difficulty:Easy Instructions Things You'll Need
Sep 23, 2011 | Specialty Electrics
Mar 11, 2010 | Specialty Electrics
Nov 11, 2009 | Specialty Electrics
Sep 11, 2009 | Specialty Electrics
Mar 12, 2009 | Specialty Electrics
Nov 13, 2008 | Specialty Electrics
380 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: