Question about Heating & Cooling
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: need wiring help for replacing
I am not sure of what help you need on it but here are the most common wiring on a stat
RC=Hot (24v for Cooling)
RH= Hot (24v for Heat)
O= Reversing Valve (Heat Pumps Only)
Hope this helps
Posted on May 11, 2008
this link has a good diagram of the wiring. It should help you.
Posted on Nov 05, 2009
For Trane sytems, B is your "Common" wire. O is your reversing valve relay, G is your fan, Y is your compressor contactor, R is Hot, Brown will not be used on your electronic tstat. X2 is your backup electric heaters. Without knowing what terminals are on your new tstat, I cannot offer more information than this. The installation manual may indicate what each terminal is controlling. I strongly suggest to write down ALL of the terminals and colors from your old t-stat and be sure to turn off the power to your air handler. Put the fan switch on your tstat to ON before turning off the power. Make sure the fan is running. Then turn the power off to your Air Handler. If your fan stops running, you have turned the power off to your tstat and are ready to start replacing it with your new tstat. I hope you find this helpful. Good Luck!!!
Posted on Feb 07, 2010
SOURCE: trane weathertron thermosatat
OK. Here is a Trane Weathertron BAYSTAT240 thermostat wiring picture. This heat pump w/ electric (emergency) heaters is running right now. Notice the G terminal has green wire, the R terminal has red wire, the white wire is jumpered from W to X2, etc. The black wire loop you see in the center hole is unconnected.
This unit is adjusted by leveling the base - loosen the screw to the left of "R" and the one to the right of "F". Twist the base clockwise to RAISE the indicator. This makes the mercury in the switch turn ON at a different temperature. Remember to tighten those 2 screws again.
You will have to experiment several times to make the unit read exactly right. If the tech installed the base exactly level, the unit would read right (it says here).
Posted on Jun 10, 2011
Tips for a great answer:
May 08, 2017 | Honeywell Heating & Cooling
Jul 13, 2017 | Heating & Cooling
Jun 13, 2013 | Honeywell RTH3100C - Digital Heat Pump...
May 23, 2010 | Honeywell Focus 6300B 5-2 Days...
Feb 06, 2010 | Heating & Cooling
Oct 16, 2009 | Heating & Cooling
May 16, 2009 | Heating & Cooling
Mar 22, 2009 | Honeywell Programmable Thermostat Heater
Mar 20, 2009 | Heating & Cooling
Feb 08, 2009 | Heating & Cooling
116 people viewed this question
Usually answered in minutes!