Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: AC unit not running
Try to off the power supply(circuit breaker) to reset the error and on again and start the unit. But if the symptom's persist you have to call for a qualified technician.
Posted on Dec 30, 2007
SOURCE: Soleus KFGHP-09-ID Mini Split
This is normal operation for these styles of minisplits. The thermostat is not in the remote but is located on the return air of the indoor coil, so the air needs to be flowing in order for the thermostat to measure the rooms temperature. Set your fan speed to auto and the fan will slow down when setpoint tempurature is met.
Tech support Soleusair
Posted on Mar 12, 2009
The fan motor is getting hot and going off on the internal overload in the motor.
This is caused by either a low voltage, a bad capacitor, or tight or dry bearings in the motor.
To check the bearings turn the power off to the unit, then spin the fan blade if it spins freely then the bearings are ok.
To check the capacitor you will need some kind of tester or you can buy a capacitor and replace it, that's what a lot of people do. They usually don't cost very much.
To check the voltage you will need a voltmeter and measure the volts at the unit.
Posted on Jun 09, 2009
The blinking light is because the unit is waiting for the outdoor unit to come on. If in heating mode, the indoor fan will not run before enough pressure and therefore heat has built up. You should check that the indoor air return sensor is not faulty and therefore preventing the outdoor unit from coming on.
Posted on Nov 18, 2009
unit may be short of gas. will run for a few mins before low pressure switch turns the compressor off. you will need to get an engineer to check gas pressure
Posted on May 23, 2010
Tips for a great answer:
Jun 05, 2016 | Heating & Cooling
Apr 25, 2016 | LG Heating & Cooling
Mar 31, 2014 | Daikin Mini Split Ceiling Suspended Units
May 03, 2017 | Heating & Cooling
Jan 19, 2011 | Heating & Cooling
Jan 07, 2011 | NewAir ACS-9001H Split System Air...
None TV is powered off. Normal operation.
Green TV is powered on. Normal operation.
Green 1. TV just plugged into AC outlet.
Wait until blinking stops before turning on (approximately 1
minute). Normal operation.
2. AC just restored after power failure.
3. TV Rebooting after System Reset was
4. TV Rebooting after power fluctuation
or receiving abnormal digital signals
from digital channel, or digital device.
5. You have begun the procedure to
update software from an authorized
flash memory device.
For detailed information, see the instructions that accompany
the authorized software update. IMPORTANT: Do not
use unauthorized software at any time.
Green TV just powered off and lamp is
Starts to blink 30 seconds after turning off TV. TV can be turned
on before blinking starts or after blinking stops, but not while the
indicator is blinking. Normal operation. hope it helps regards shaun
Green TV powered off and auto-on timer is set. Normal operation. TV can be turned on at any time.
Dec 06, 2010 | Mitsubishi Televison & Video
21 people viewed this question
Usually answered in minutes!