Question about Square D Qob120 1pole 20amp 120v Circuit Breaker
You have 2 circuits that feed the garage , not a problem , the one that you stated tripped often is the one we are concerned with . now do you remember which one that was , if so we need to start there . the first thing to determine is the load on the circuit large enough to to justify tripping of the breaker , breakers tripping is not always an indication of a problem it simply means it is doing its job sometimes . To determine the load turn on all the devices normally on in the garage and get or borrow a amp probe a wrap around is the easiest to use open the breaker panel that feeds the garage and wrap the amp probe around the wire leaving the panel that feeds the circuit to the garage that is the one that trips see if the load is close to the rating on the breaker , if it is then the breaker is doing its job and the only solution it to split the load . now if the load needs to be split then don't forget you said you had two circuits feeding the garage so you might be able to divide the load more evenly between the two you already have before you have to run additional circuits , tripping of breakers is not always a bab thing in most cases in my 40 years of being an electrician it is a case of them doing there job and the load needs to be more evenly divided if this does not help let me know and we will dig deeper
Posted on Jan 30, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 01, 2013 | Electrical Supplies
Mar 05, 2011 | Electrical Supplies
Oct 24, 2010 | Gb Electrical 100 Amp GE Load Center
Oct 11, 2010 | Connecticut Electric Square D Packaged...
Aug 30, 2009 | GE Nautilus 24" Built-in Dishwasher
Jul 15, 2009 | Blue Sea Sea 3082 Dc 10 Position Toggle...
Jan 29, 2009 | Dayton 3VU34 Heater
Nov 06, 2008 | 2000 Oldsmobile Alero
Aug 21, 2006 | Hotpoint 23 in. BF50 Built-in Dishwasher
142 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: