Question about Haier Energy Star ESA3183 Air Conditioner
I have the Model# MBE2000 & CAPF4860D6A 16 seer 4 ton heat pump. After two-four hours the heat pump blows the fuse on the circut board in the indoor unit. Is very annoying. I have been replacing these 3 amp fuses at a rate of 5 per day. Started satruday when temps were down in 20's. Furnace runs normally untill the fuse blows then shuts off. Circut breakers are not tripping or anything. Tried to un plug the hudistate and that didn't help. Please any help would be nice. 50 degree mornings ****.
I would suspect you have a problem in the defrost circuit of your heat pump. there are a couple of things you can try. first just run the system on emergency heat and see what happens. you could have a defrost board that is shorting when it kicks into defrost. it sends a signal back to the furnace so it will come on during defrost. if you do not blow a fuse as long as you are running in emergency heat, i would suspect the defrost control board. also you could have a dead short in the wire that runs from the "w" terminal on furnace control board, out to the heat pump. keep in mind that any of the wires could be the cause and i am just tying to give you the most common things. your furnace will still run if you unhook all the low voltage wiring out at the heat pump. if you do this and stop blowing fuses. you know it is something on that wiring. goodl luck.
Posted on Jan 27, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 10, 2015 | Goodman Manufacturing Goodman...
Aug 20, 2014 | Heating & Cooling
May 21, 2014 | Goodman 3 Ton 14 ee Goodan Heat Pump...
Feb 23, 2014 | Goodman Manufacturing Goodman GPH1348H41...
Jan 17, 2014 | Goodman Manufacturing Goodman GPH1330M41...
Nov 29, 2013 | Goodman Manufacturing Goodman GPH1530M41...
Feb 18, 2011 | Heating & Cooling
Aug 11, 2009 | Heating & Cooling
Jul 02, 2008 | Amana PTH123B25AJ Heat Pump Air...
729 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: