Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Check regulator on the unit.
Check pilot unit on the heater
use soapy water to check for leaks if see bubbles turn off main gas supply valve.
always turn off gas supply before any checks or repairs are made
when all else failes call your local gas provider to check heater and gas supply
Posted on Dec 16, 2008
If you are not getting any codes from the board, then the furnace is not getting a call for heat from the thermostat. A wire may have come off, the thermostat not properly wired, or a break in the stat wire. On a call for heat, you should have 24vac between W and C on the circuit board. This will let you know if you are getting a call for heat all the way back to the furnace.
Posted on Oct 07, 2009
Sounds like the pilot is dirty....when dirty it gets smaller and lazy...tends to go out easy...try gently tapping it with a screwdriver...make the pilot bluer and bigger....when it's dirty it has yellow tips or yellow completely , the pilot should fully envelope the thermocouple as well
Posted on Nov 01, 2009
Tips for a great answer:
Mar 02, 2015 | Heating & Cooling
Mar 09, 2013 | Heating & Cooling
May 17, 2010 | Heating & Cooling
Mar 07, 2010 | Ruud UBHC Air Conditioner
Jan 27, 2010 | Heating & Cooling
Nov 16, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 07, 2009 | Goodman GMS90703BXA Heater
Oct 18, 2008 | Ruud Heating & Cooling
Sep 05, 2008 | Heating & Cooling
318 people viewed this question
Usually answered in minutes!