Question about Heating & Cooling
Hi, welcome to Fixya. First thing that I would recommend checking is the filter and air flow in general. The furnace may be overheating, cooling enough to run, overheating and so on. The second thing ( you didn't say so I'll assume it's gas heat) I would check is the tube coming off of the inducer. The inducer is the little blower that generally comes on before anything else on start up. There is a small rubber tube coming off of it. Pull the end of the tube connected to the inducer, then taking a straightened paper clip or similar poke the orifice in the nipple that the tube came off to clear any obstruction. Then retry the furnace. Let me know if this helps please.
Posted on Jan 26, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 30, 2016 | Heating & Cooling
Feb 01, 2015 | Heating & Cooling
Jan 31, 2015 | Heating & Cooling
Oct 02, 2010 | Sharp AF-R100DX Air Conditioner
Aug 18, 2010 | Intertherm Heating & Cooling
Aug 31, 2009 | Heating & Cooling
May 24, 2009 | Heating & Cooling
88 people viewed this question
Usually answered in minutes!