Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: 6 blinks
sounds to me like i wish i could find out if this is new install or if the electric has been changed recently,,,sounds like reversed polarity on the plug,,,which means the white and black wires need to be swapped. If there has not been change recently than u need to see the other post i made on goodman about the combustion fan motors and there types and fixes. But almost certain that is reversed polarity. good luck
Posted on Oct 25, 2008
NO BECAUSE THE BOARD IS TELLING THE FANS TO STARTARE THE CONTACTS FUSED TOGETHER OR STUCK IN THE CLOSED POSISTION CHECK THIS FIRST
Posted on Aug 10, 2009
PRSSURE, DRAFT SAFGUARD, AUX-LIMIT SWITCH(WHEN USED)OR BLOCKED VENT
SWITCH(WHEN USED) DID NOT CLOSE OR REOPENED (DOWNFLOWONLY)
If open longer than five minutes, inducer shuts off for 15 minutes
* proper vent sizing
* defective inducer motor
* restricted vent
* excessive wind
* low inducer voltage(115VAC)
* defective blower motor or capacitor
* defective pressure switch
* inadequate combusstion air supply
* disconnected or obstructed pressure tubing
If it opens after trial for ignition period, blower will come on for
90 sec. recycle delay.
Check your air filter for blockage, check pressure switch for a buildup of moisture. Make sure your inducer motor is turning and creating a vacuum to the pressure switch. Make sure all venting is clear and free of water or debris. Make sure there is no water in inducer motor and all drains are draining.
Posted on Jan 28, 2010
SOURCE: I turn the thermostat on
This on blink of the light is a system lockout. It is caused when no gas is released to light the burner. The first thing to try is to turn the power off to the unit make sure your thermostat is off also. Turn the unit back on and make sure your gas is turned on. Then turn on the thermostat. Try this 3 or 4 times to make sure there is not air trapped in the gas line preventing ignition. If it lights after doing this you should check for a small gas leak at all fittings and shut off valves. The reason for this is to make sure you do not have a slow leak. If you smell gas turn off the furnace and your gas main valve and call a repair person. If you are unable to turn off the gas you should call the utility immediately. The cycle for your furnace is as follows. When your thermostate demands heat a signal is sent to your circuit board in the furnace and it turns on a exhaust fan to cause a draft to push air out the flu. (this fan is on 92% and higher funaces) This fan has two vacume lines that run to two vacume switches one is for the presence of vacume the other is for sensing the release of vacume. These are low voltage switches hooked into the 24v system. If the fan works and the switches sense vacume it then turns on the gas igniter this will be a glow bar and you will see it glowing. This in turn has a sensor that near it that can sense the heat from the glow bar igniter and it in turn turns on the gas by sending the 24v signal to the gas valve. If after 8 to 15 seconds the flame does not come on the system will reset and try again for a total of 3 times. If any of the above systems do not work your furnace will lock out because it thinks there is gas being dumped into the furnace. If the exhaust fan comes on you have 24v going thru your thermostat to the furnace. Then the vacume switches have to work. One is normally open the other normally closed. If you have a volt/ohm meter which can be purchased for as little as 10 to 15 dollars at a hardware store you can check these switches. You will need to set the thermostat to off and turn off voltage to your furnace for safety. Then locate the two switches by following the black rubber vacume lines from the exhaust fan housing to the switches. Pull the wires off the switches and with the meter set on ohms place the leads on the two terminals. While the meter is hooked up pull the vacume line off the fan housing and **** air in and out of the line the meter should swing back and forth as it senses vacume and the lack of it. If it does it is working. Then do the other vacume switch. Make sure to keep your wires and where the vacume lines go straight. You will also see a sensor mounted above and center where your burners are at it will have two wires going to it and it will be round it should show continuity ck it by removing the wires form it and touching the meter leads to the connectors the meter should respond showing continuity. There are two others under the burners on each side ck them the same. If any of your sensors have a pop ot button in the center press in on it yours should not this is an older version yours should be self reseting. The only other sensor is located in the blower for circulating the air. It is located on the right hand side of the blower housing with a red and yellow wire going to it. It has a reset in the center this sensor is used to trip if the heat in the blower housing gets to hot. This happens when the blower motor quits or is not able to move air fast enough due to restrictions. If the sensor has tripped you will feel and should hear an audible click when you press on the center button also if you check it for continuity it will show none and when you press the button it will show continuity. The next thing is the gas valve If all of the above work it is either the gas valve not opening or your circuit board. All of the parts are inexspensive until you get to the circuit board and the gas valve. The gas valve should be replaced by a repair person. You can replace everything else just make sure you turn off the power and pay close attention to the wiring. I hope this helps good luck. But not to down play the above make sure te top panel is in place put your hand on the gas valve and have someone turn on the thermostat. If the exhaust blower comes on and the ignitor glows you should then feel a click from the gas valve if you do not it us normally the circuit board. If you do and it still doesnt light you have no gas coming to your furnace. I hope this helps good luck
Posted on Sep 11, 2010
these codes are on the inside panel of the front cover of the furnace. lift off and look inside.there should be a code explain chart on the panel by the light. this panel will need to be replace correctly for the furnace to work as there is a door switch.
Posted on Feb 01, 2011
Tips for a great answer:
Jul 13, 2016 | Heating & Cooling
Nov 21, 2015 | Heating & Cooling
Nov 28, 2013 | Sony Televison & Video
Jan 31, 2011 | Heating & Cooling
Jan 22, 2011 | Heating & Cooling
Oct 23, 2010 | Ruud Heating & Cooling
Sep 15, 2008 | Ruud UBHC Air Conditioner
Jan 19, 2008 | Ruud UBHC Air Conditioner
Oct 20, 2017 | Heating & Cooling
Oct 20, 2017 | Heating & Cooling
231 people viewed this question
Usually answered in minutes!