Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: luxaire model 50a50 209
Check the 3-5 amp fuse on the control board, if the fuse is bad then there is a short somewhere in the low voltage circuit, usually in the thermostat wires. If the fuse is good check for 24 volts atbthe R and C terminal, if no voltage there then the board is bad and must be replaced.
Posted on Nov 26, 2012
Tips for a great answer:
Mar 18, 2017 | Heating & Cooling
Dec 05, 2016 | Heating & Cooling
Jan 23, 2016 | Heating & Cooling
Nov 21, 2015 | Heating & Cooling
Oct 03, 2015 | Cars & Trucks
Apr 13, 2014 | Carrier Furnace Control Board Bryant...
Mar 07, 2014 | Heating & Cooling
Nov 05, 2013 | Heating & Cooling
26 people viewed this question
Usually answered in minutes!