Question about Caterpillar CAT 150 KW Natural Gas Standby Power Generator
Relocated and replaced gas regulator for same problem told by cat additional piping needed between regulator and engine. relocated 50 feet away. started and ran good but after replacing governor the problem returned.
Install a pressure gauge at the gas inlet regualtor, conform it isn't less than specs normall 11-13" WC pressure. test this when it is surging, it sounds like fuel, or also incorrect governor gain setting
Posted on Nov 17, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 08, 2015 | Generac XG8000E - 8000 Watt Electric Start...
May 04, 2017 | Eaton Electrical Supplies
Sep 16, 2013 | Generac Power Systems Commercial Series...
Jun 27, 2013 | Kohler 30RESA 30kW Standby Generator...
Jul 27, 2012 | Electrical Supplies
Jul 03, 2017 | Grilling
Sep 05, 2011 | Robin Subaru RGX7100 7100 Watt Gas...
Mar 01, 2011 | Water Heaters
Apr 27, 2010 | LG WD-3243RHD Front Load Washer / Dryer
May 17, 2009 | GE 30 in.JGP330 Gas Cooktop
139 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: