Question about Heating & Cooling
The boiler does not work and is showing an f7 then f5 fault code , the hotwater valve is continually closing even when switched on or off ,it doesnt try to open.
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I have a honeywell smartfit
I had exactly the same problem. F4 code says the control valve has jammed --- but it hadn’t.
I ended up having to swap out the room controller and the base unit (I bought the pair since it was winter and I couldn’t ‘eff’ about)
On investigating (well, you have to don’t you?) I could find no obvious fault but did notice that a large electrolytic capacitor was across the actuator motor.
Since these things work by reversing the supply polarity to the motor to drive the actuator one way and the other it strikes me as strange that a polarity sensitive component, one that must be always connecter positive to positive, is used in the way that it is.
Bottom line, tough luck, mate. Replace the units.
Posted on Jul 31, 2008
What kind of boiler are using is this boiler a on the demand electric or gas? You need low voltage wires. If you get me make and model # of off boiler i can try and find wiring diagram . Tell me a little more about you heat system to. Like baseboard heat or in floor how many zones
Posted on Jan 16, 2009
You may have a broken thermostat wire. Disconnect the wires from the thermostat and please note what colors are hooked to which terminals. Cross the R and W wires and see if your heating system turns on. If it does not, you have a broken wire or bad connection at the heating system. If it does start, you have a bad thermostat or bad connection at the thermostat.
Posted on Nov 30, 2009
Tips for a great answer:
Aug 14, 2017 | Honeywell Programmable Thermostat Heater
Jan 23, 2014 | Honeywell Programmable Thermostat Heater
Jan 21, 2013 | Heating & Cooling
May 22, 2011 | Honeywell Heating & Cooling
Dec 02, 2010 | Heating & Cooling
May 20, 2010 | Quasar HQ2051TH Air Conditioner
Mar 10, 2010 | Honeywell Heating & Cooling
Jul 30, 2008 | Honeywell Heating & Cooling
May 21, 2008 | Honeywell Heating & Cooling
Sep 26, 2017 | Honeywell Heating & Cooling
129 people viewed this question
Usually answered in minutes!