Question about Heating & Cooling
Thanks for your Question,
B- is your common leg,
RH- is your hot to heating
RC1- you will not need
RC- you can use if you remove the jumper for cooling
Y1- you will not need
G- is your fan
O is not needed, wires should be hooked in as follows,
RH- red wire, heating
RC- Yellow wire, Cooling
G- Green wire, Fan
B- Blue wire, for common leg, this one might be a different color so make sure at the furnace which T-Stat wire is connected to Common, you should check all the wiring at the furnace to make sure this pattern of wiring is followed, it should be standard practice to hook them up this way, but not all installers do it, thanks again, please rate this,
Posted on Jan 25, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 16, 2014 | Honeywell T827K1009 Mercury Free EconoStat...
Sep 14, 2014 | Heating & Cooling
Apr 27, 2013 | Honeywell Heating & Cooling
Jun 12, 2011 | Heating & Cooling
May 24, 2011 | Heating & Cooling
May 23, 2011 | Heating & Cooling
Jan 11, 2010 | Heating & Cooling
Nov 10, 2009 | Heating & Cooling
May 07, 2009 | Honeywell Heating & Cooling
Jan 21, 2009 | Heating & Cooling
Jan 22, 2017 | Slant Fin Heating & Cooling
313 people viewed this question
Usually answered in minutes!