Question about Heating & Cooling
Thanks for your Question,
B- is your common leg,
RH- is your hot to heating
RC1- you will not need
RC- you can use if you remove the jumper for cooling
Y1- you will not need
G- is your fan
O is not needed, wires should be hooked in as follows,
RH- red wire, heating
RC- Yellow wire, Cooling
G- Green wire, Fan
B- Blue wire, for common leg, this one might be a different color so make sure at the furnace which T-Stat wire is connected to Common, you should check all the wiring at the furnace to make sure this pattern of wiring is followed, it should be standard practice to hook them up this way, but not all installers do it, thanks again, please rate this,
Posted on Jan 25, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 12, 2011 | Heating & Cooling
May 24, 2011 | Heating & Cooling
Oct 23, 2010 | Hunter Fan Company 5/1/1 Programmable...
Dec 05, 2009 | Hunter Fan Company 5/1/1 Programmable...
Aug 21, 2009 | Hunter Fan Company 5/1/1 Programmable...
Apr 30, 2009 | Hunter Fan Company 5/1/1 Programmable...
Mar 08, 2009 | Hunter Fan Company 5/1/1 Programmable...
Jan 22, 2009 | Honeywell Programmable Thermostat Heater
Feb 12, 2008 | Honeywell CT87B ROUND HEATING&COOLING...
Feb 07, 2008 | Hunter Fan Company 5/1/1 Programmable...
318 people viewed this question
Usually answered in minutes!