Question about Humidifiers
Newer < 2 years. Water supply line is ok. Wiring at solenoid,at humidistat, and at furnance are intact. My guess is that automatic humidifer control or solenoid are not functioning - How do I determine which?
Thanks for your question,
first you need to determine if you have 24 volts from the transformer, if you have knowledge of electrical meters then this should be fairly easy, if not then you will need to do a little rewiring to find out if it is the solenoid, first you will need to do is shut the power off to your furnace, then get some t-stat wire, long enough to reach from the solenoid to the transformer, splice together the new wire to the wire from the solenoid, now take the other end of the wire, take the leads off the transformer (low voltage side) and hook the new leads to it, make sure the water is on, now turn the furnace back on, and if the solenoid is good the water will flow, if it doesnt, then you will need to replace the solenoid, if the solenoid does work then you know your problem lyes with the Humidistat, and you will have to replace that, but you need to determine if you have 24 volts from the transformer first, hope that helped, let us know and please rate this, thanks again ,
Posted on Jan 25, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 30, 2013 | Aprilaire 700 Humidifier
Jan 29, 2008 | Aprilaire 550 Humidifier
Dec 31, 2011 | Honeywell Humidifiers
Apr 03, 2010 | Honeywell HE360A1027 Whole House...
Jan 06, 2010 | Aprilaire 600 Humidifier
Dec 28, 2009 | Honeywell HE260A1010 Whole House...
Nov 28, 2009 | Honeywell HE260A1010 Whole House...
Oct 12, 2009 | Honeywell HE220A1019 Whole House...
Jan 24, 2009 | General Filters 1042-LH Humidifier
Dec 15, 2007 | Aprilaire 550 Humidifier
Jul 11, 2017 | Humidifiers
768 people viewed this question
Usually answered in minutes!