Question about Heating & Cooling
Thanks for you question,
First thing you will need to look at is the Breakers in the breaker panel, is the breaker tripped ? make sure by flipping the breaker to off then on, sometimes it doesn't show as tripped, if that's ok, then the next thing to check is the fuses in the disconnect next to the condenser, make sure you shut the breaker off to the unit first, then remove the fuse and Ohm check them if you have no reading on either one, then you should replace them both, after replacing them, turn the power back on and hopefully your unit will fire right off ! if these first things dont work, let us know we can go deeper into what else might be the problem, thanks again,
Posted on Jan 25, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 16, 2014 | Refrigerators
Dec 10, 2010 | Maytag MBB1952GR Bottom Freezer...
Oct 06, 2010 | Sub-Zero Bottom Freezer Refrigerator
Apr 07, 2010 | Sub-Zero 695/O Side by Side Refrigerator
Feb 21, 2010 | KitchenAid Superba Architect KSCS25INSS...
Jan 30, 2010 | Refrigerators
Jan 21, 2010 | Kenmore 55612 / 55614 / 5561 / 655619 Side...
Nov 23, 2009 | Air Purifiers
May 08, 2009 | Refrigerators
127 people viewed this question
Usually answered in minutes!