Question about LG LSC121PMA Split System Air Conditioner
Within 5 minutes of turning on the air-con, it will turn itself off. In this time it will not have any cooling effect at all. When the aircon shuts off, the power light will flash.
The outdoor indictor light on my lg split comes on after some minutes on the one inside and the cooling has reduced please can any1 tell me what the problem is
Posted on Aug 29, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
This is possibly either a complete outdoor pc board error or an E-Prom error on the indoor pc board. You can try shutting down supply power completely for a minute and then switch on. These units also have a delay timer system which does not like to be switched on, off repeatedly in a short period. Please also check for reset button on the outdoor pc board. Hope this helps.
Posted on May 14, 2009
Sounds like your aircon is stuck on heating mode. Or. The outdoor fan speed is affected by ambient temperature, or low refrigerant. In heating mode the indoor fan will come on for a while to sense temperature and will then wait for the outdoor unit to pump up pressure and build up heat.
Posted on Mar 04, 2009
Please specify the make and model of your unit.
If this is a LG inverter model.
The six flashes of the indoor unit light indicates a CH 06 alarm.
This alarm state indicates that the indoor unit pipe temperature sensor has measured a temperature out of range or the unit is protecting itself from this low temp state. Indoor unit coil temperature to low. Should it have reached a temperature of -5°C for longer that 30sec it will switch the machine off.
It could indicate that the unit refrigerant charge is too low or the sensor has gone out of calibration.
It should measure 5kΩ @ 25°C
Posted on Mar 22, 2010
SOURCE: LG split inverter model LSL122V3
Communcation error between in and out.
Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Dec 31, 2010
E-5 -Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 03, 2011
Tips for a great answer:
Apr 28, 2017 | Rover Cars & Trucks
Aug 02, 2014 | Honeywell Heating & Cooling
Jan 24, 2013 | Fujitsu 24C1 Air Conditioner
Jan 03, 2013 | Heating & Cooling
Jul 05, 2011 | GE AEW12AN Air Conditioner
Jun 15, 2011 | Sanyo Heating & Cooling
May 15, 2017 | Heating & Cooling
Oct 22, 2010 | Samsung DLP HL-P5663W 56" TV
956 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: