Question about Goldstar Heating & Cooling
Unit has not been used in a few years blows cold air when on ac but no hot air at any setting. What part(s) could it be. Would like to troubleshoot or replace easiest or most likely part first and work forward from there.
Posted by Anonymous on
If your thermostat is working on the Heat cycle (listen for "click" when turned up and down on Heat), then your heating coil assembly is probably bad. The heating coil is in series with a Fusible Link and a Bi-metal thermostat, if any of these three fails, there will be no heat from the coils.The Link and Bi-metal Thermostat are made up as part of the heater coil assembly.
Posted on Nov 26, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If you have a reverse cycle unit (heat pump) your compressor and your fan should be running. You need to determine if your compressor is running.
Posted on Nov 08, 2007
Check your thermostat and mode selector setting, thermostat setting should be set at warmer and mode selector setting should be at low heat or hight this is applicable for manual unit.
If it is a remote control just set the remote to heat mode.
Posted on Jan 12, 2008
When the unit is running, go outside and put your hand near the condenser fins, this air that comes out should be slightly warmer than the ambient temp. If it is not you will need to take the unit out of the window and out of its outer case and clean the condenser fins from the inside, this is no easy task as it is very hard to reach. You will want to get a small (toothbrushed sized) brass bristled brush with a long handle. Make sure the evaporator coil (in the front) recieves the same attention and wash the mesh filter that goes in front of the evaporator. Re- assemble and enjoy the cold air.
Posted on Jun 07, 2009
your fan motor outside is going bad, have a service company change it out for you.
the motor stopped working and that overheated the compressor shutting it down on thermal cutout, and it will only come on once it cools down
Posted on Jul 01, 2009
Tips for a great answer:
Dec 08, 2013 | Friedrich CP06C10 Wall/Window Air...
Nov 24, 2013 | Soleus 10,000 Btu Portable Ac Air...
Jul 20, 2011 | Goldstar R2403 Air Conditioner
Apr 27, 2011 | Goldstar KG6000R Window Air Conditioner
Dec 13, 2010 | LG Heating & Cooling
Jul 28, 2009 | Goldstar GW-HD5000 Window Air Conditioner
Feb 09, 2009 | Honeywell Programmable Thermostat Heater
Sep 04, 2008 | Goldstar Heating & Cooling
108 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: