Question about Heating & Cooling
Welcome to Fixya. It sounds as if one of the limit switches has opened. Did you have a dirty filter? Limit switches are mounted on the fire box(box around the burners) and around the middle of the furnace in front. They may or may not have a reset button on them. First turn off the power. Then if you see the limits with buttons go ahead and reset them. If none of the limits has a button on it tap the metal next to it (don't hit the limit or it will break) this may jar it enough to reset it. You can also jump them out by removing the wires from the terminals and joining them together with some elec. tape. I DO NOT recommend running your furnace with a limit bypassed. This is for diagnosing only. Please let me know if this helps or not.
Posted on Jan 25, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 10, 2016 | Rheem 2.5 Ton 13 Seer Heat Pump -...
Oct 26, 2013 | Ingram's Water and Air 100,000 BTU RHEEM...
Jan 19, 2011 | Weather King 10AJA3601AH Air Conditioner
Jan 01, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Sep 13, 2009 | Heating & Cooling
Jul 12, 2009 | Ruud UAKA037 Air Conditioner
Mar 22, 2009 | Heating & Cooling
Jan 31, 2009 | Heating & Cooling
Jan 07, 2009 | Heating & Cooling
Jan 06, 2009 | Heating & Cooling
81 people viewed this question
Usually answered in minutes!