Question about Rinnai RHFE-1004FA 38,400 BTU Energy Saver Ductless Heater - LP Gas
When the room temperature has been reached the flame lever reduces to low but never shuts completely off. When I increase the temperature setting the flame increases and the unit sends out more heat.
Is there a chance there is a draft around the room temp probe? It is down low on the right side of the heater. If there is a draft the room sensor is fooled and keeps running the unit. You should be able to prove the room sensor by putting your hand over it after the stove has been running for a while. This should shut the stove down. If not there is a problem with the room sensor.
Posted on Feb 26, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 15, 2015 | Procom 10K BTU, Vent Free, 2 Plaque...
Feb 22, 2015 | Cozy Heating & Cooling
Dec 01, 2013 | Imperial Kitchen Appliances - Others
Oct 12, 2013 | Amana Heating & Cooling
Oct 31, 2011 | Intertherm P3RA-048K Air Conditioner
Jan 23, 2011 | Heating & Cooling
Dec 12, 2010 | Kitchen Appliances - Others
Nov 08, 2010 | Dyna-Glo Heating & Cooling
Jun 18, 2010 | Rinnai Vent Free Gas Heater/
Aug 02, 2009 | Heating & Cooling
218 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: