Question about Gibson Heating & Cooling
Fan relay stuck in & control fuse might be blown. see if you have 24 volts at outside unit.
Posted on Aug 13, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Carrier air handler tonnage?
That is a fairly large difference. It is usually ok to have the inside evap. coil and blower up to 1 ton larger than the outside condenser. That will make the unit slightly more efficient as well as less likely to freeze up on low airflow situations. It is not recommended to install a new condenser on an old evap coil. There has been a lot of changes to the design of the coils in the last little while. For example a 10 year old 2 ton coil may only have 3 cubic feet of volume but a new 2 ton coil may have 4 cubit feet of volume.
There are many factors that may have infulenced the decision on what size condenser to install. Many of which can only be done by visiting the home and doing alot of work, checking the duct sizing bioth supply and return, inspecting the insulation and windows of the home etc. etc. Most of the time that never gets done. You can blame the contractor for not doing a complete check, but at the same time you can blame the customer because many contractors that are that good loose the job to a cheaper bid that did not no any of the research. It is a catch 22 for everyone involved.
There is ALOT more to sizing equipment that many people think, sadly that also includes many HVAC contractors. Way too many people use "rule of thumbs" or flat out "guess".
Sorry for the rant but your queston can only be answered by a good well educated HVAC contractor visiting your home. That type of a contractor is getting hard to find these days in such a price competetive world.
Posted on Oct 14, 2008
SOURCE: the air handler won't shut off
As long as the t-stat fan switch is in the auto position the problem sounds like fan relay is stuck. It looks like a little black box about 2 inches square. Has 5 positions on it two of them are for 24 volts.
Be sure you turn off power before pulling it out. Make note of the arrangement of the wires maybe label as you remove them. ken
Posted on Dec 27, 2008
Tips for a great answer:
Mar 29, 2015 | Heating & Cooling
Aug 26, 2014 | Heating & Cooling
Jul 31, 2012 | Goodman Heating & Cooling
Jul 13, 2011 | Heating & Cooling
Jan 02, 2011 | Goodman CLJ30AR32 Air Conditioner
Apr 03, 2010 | Ruud Central System Air Conditioner
Jul 20, 2009 | Heating & Cooling
May 27, 2009 | Carrier 52CQ315 Air Conditioner
Apr 11, 2009 | Ruud Handler Air Conditioner
95 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: