Question about Intermatic EH40 Energy Controls - Electronic Time Switches - Water Heater
My buttons on the heater control for changing the heat from defrost to vent to the floor do not work, it basically blows out all three areas at the same time. What is the problem.
The aperage at start up when you turn on the heater are to great. The load at start up is greater than when it is actually running which in my opinion means the load is greater than the EH40 amperage rating is. In short term, the EH40 contacts are not able to handle the load. You need a higher rated control, it wasn't sized up correctly by your vendor,
Posted on Jan 25, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 17, 2015 | Hardware & Accessories
Feb 15, 2014 | Amerec 4.5KW Heater w/ Built-in Dial...
Jun 24, 2013 | Paragon Hardware & Accessories
Jun 29, 2011 | Paragon 8145-20 Defrost Timer
Feb 15, 2011 | Frigidaire Maytag R0131577 215846602...
Nov 20, 2010 | Grundfos The UP1510B5ATLC 125th HP 1...
Nov 19, 2010 | Intermatic HEATER DELAY SHUT OFF SWITCH...
Sep 29, 2010 | Paragon 8145-20 Defrost Timer
Jan 11, 2010 | Honeywell International Heil Quaker...
Oct 22, 2009 | Broan-NuTone Broan QTXE150FL Bathroom...
86 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: