Question about Grohe Integrated 1/2'' Shower Thermostatic Rough-In Valve With Stops - 3412
IS THE MAIN CARTRIDGE THE PROBLEM OR IS IT THE STOPS OR CHECK VALVE THIS IS A THERMOSTAT VALVE # 34 434 000 THE CARTRIDGE IS ALOT OF MONEY SO I DO NOT WANT TO INSTALL AND NOT FIX PROBLEM THANKS FOR HELP RICK
Yes this is definately the cartridge.You might not have to replace the cartridge.First take the cartidge out and see if their is any dirt causing the water to pass thru the spout.If thiers nothing obstructing the cartridge than you will need to get a new one.
Posted on Feb 02, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 04, 2015 | Honeywell Water Heaters
Apr 09, 2015 | Water Water Heaters
Mar 14, 2015 | Water Water Heaters
Nov 14, 2014 | Cadet Heater. Soft Heat 71 in. 1,250-Watt...
Oct 30, 2013 | Rheem Water Heaters
Dec 10, 2011 | Grohe Grohmix Thermostat Valve & Trim -...
PROBLEM #1 - HOT SURFACE IGNITOR DOES NOT GLOW RED
(Remember to wait for purge time, 17/34 seconds, on models so equipped).
A. No main power
B. Faulty transformer
C. Faulty thermostat
D. Faulty limit switch
E. Faulty blower interlock switch
F. Faulty hot surface ignitor
G. Faulty ignition control
Perform normal system checks of main power, transformer, thermostat, limit
switch, blower interlock switch, and replace faulty component.
With power on and thermostat set at its highest position, check voltage
between "TH" and "TR" on HS780 ignition control. If 24 volts is not present
check output at transformer. If no, replace transformer. If transformer
checks out OK look at other controls in the 24 volt circuit I.E.: thermostat,
limit switch, blower interlock switch. Check for 120 volts between "neut"
(L2) and "120" (L1). Check for 120 volts at the ignitor across "IGN" and
"IGN" terminals on the HS780 ignition module. If 120 volts is present,
replace ignitor. If no, replace the 780 series module
PROBLEM #2 - IGNITOR GLOWS RED BUT MAIN BURNER
A. Improper ignitor alignment
B. Faulty ignition control
C. Faulty gas valve
D. High inlet gas pressure
E. Polarity reversed
F. No earth ground
Check for availability of gas at gas valve. Make sure the manual valve
upstream of the gas valve and the gas valve are in the full on position. Also
make sure gas is being supplied to the system at the proper pressure, too
high will lock-up the valve.
Check proper polarity of "NEUT" and "120" on the ignition control by reversing
the wires, if reversed gas valve will not open. If this does not solve the
problem, replace wires as they were.
Check for proper ignitor position.
Check for a good earth ground by using a meter connected between L1
and furnace chassis. Should read 120 volts, if no, check and/or repair ignition
ground wire or ignition control mounting screws.
CAUTION POLARITY MUST BE OBSERVED
Check for 24 volts at the gas valve terminals; "1" and "2" on a 7200 series,
"M" and "C" on a 7100 series, "TH" and "TR" on a 7000 series. If yes,
check wire integrity or change the gas valve. If no, change the 780 series
That is pretty much all of the troubleshooting required.
Thanks for choosing FixYa,
Feb 14, 2011 | Rheem 40 Gallon FVR NATGAS Low WATER...
Feb 17, 2010 | Grohe Integrated 1/2'' Shower Thermostatic...
Oct 24, 2009 | Rheem 50 Gallon FVR NATGAS Water Heater...
Mar 26, 2009 | Grohe Grohmix Thermostat Valve & Trim -...
1,019 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: