Question about Flotec 1 Hp Deep Well Pump
Model c48k2ec15 convertible hydroglass. This is a pump that sits on top of a pressure tank in the basement. 1hp
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
if the pump is working correctly, it can either be, need more water to prime it, or something in the well, such as low water, plugged filter, etc....sometimes when you have a system that is intermittently used, it can take 20 or 30 minutes of continuous priming to get it to pull, enough water to maintain the prime.
Posted on Apr 06, 2009
SOURCE: air in lines
SOUNDS LIKE A CRACKED SUCTION STUB OR LOOSE THREADED FITTING SUCKING IN AIR.
OR THE CHECK VALVE IS FAILING AND ALLOWING THE WATER TO LEAK BACK SLIGHTLY OR ALL THE WAY BACK. YOU CAN ALSO ADD A FOOT VALVE AT THE END OF THE PIPE.
LONG SHOT, BUT THE BLADDER TANK IS CHARGED WITH AIR AND MAY HAVE A HOLE IN THE BLADDER CAUSING THE TANK AIR TO ENTER THE SYSTEM. SHOULD RUN OUT QUICKLY THOUGH. HOPE THIS HELPS, JODY
Posted on Jul 19, 2009
The pressure tank must have a certain amount of air in it so pump doesn't cycle as you say. The new pressure tanks have a bladder that separates air from water and keeps the pump from cycling so much. Make sure your pressure switch on the pump is OK--ie doesn't have burned contacts!
Posted on Mar 01, 2010
SOURCE: The pump operates, but will
It is possible that sediment has clogged the opening that supplies the sensing pressure to the switch. Shut down the pump, open a valve to drop pressure completely, remove the tube where it enters the pump body and stick a small wire just into the hole, once that is clear, see if you get water to come out when the pump is activated. Next, you can see if the entire sensing tube is clear by disconnecting the end on the pressure switch and ensuring flow there. Lastly, make sure there is nothing plugging the inlet at the pressure switch. This has a rubber diaphragm in it, so do not stick anything up inside, just ensure that there is no rust/corrosion in the inlet area.
Posted on Dec 27, 2010
SOURCE: I replaced old pump w/
The water and therefore the pressure has to be going somewhere. If you are sure that there are no leaks in the house or outside, then the water is going back into the well. There is a check valve either in the suction line of the pump between the top of the well and the pump or down in the well.
If this check valve fails, it allows water to go the wrong way and back to the well. The result is that you lose pressure.
Secondly, you have to be sure that there are no air leaks between the top of the well and the inlet to the check valve. Leaks in that piping will make repriming difficult.
Write back with more and I'll try to help more.
Posted on Jan 22, 2011
Tips for a great answer:
Dec 24, 2013 | 1997 Mercury Cougar XR7
May 17, 2013 | Motorcycles
Apr 13, 2017 | Cars & Trucks
Dec 08, 2012 | 2001 Mazda Protege
Aug 10, 2012 | kawasaki Motorcycles
May 22, 2012 | 2002 Honda CBR 1100 XX Super blackbird
May 27, 2010 | 2004 Chevrolet TrailBlazer
Nov 26, 2009 | 2002 Yamaha YZ 426 F
Feb 03, 2009 | 1995 Chevrolet Lumina Apv
37 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: