Question about Intertherm P3RA-060K Air Conditioner
My husband tried to put in a new digital thermostat but it turned out to be not compatible now we are trying to put the old one on and it doesn't now seem to work i think it is wiring could some one help
Thanks for your Question,
A question or two for you, when your husband was hooking up the new stat, could he have inadvertently touched the low voltage wires together ? if so have you checked the circuit board at the furnace to see if the fuse is blown ? The fuse looks like a automotive fuse on the board, look carefully sometimes its a little hard to find it, take the fuse out and look at it, you can tell if its burned out, I would almost be certain that this is where your problem is at, replace the fuse with another 3amp fuse, make sure the power is off before doing this, and with the power off hook in your new t-stat, bet it will work for ya ! Or hook back up the old one, in any case you seem to have a power issue, hope this was of help, thanks again for your question,
Posted on Jan 24, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 02, 2016 | Heating & Cooling
Dec 16, 2013 | Intertherm P3RA-048K Air Conditioner
Jun 19, 2011 | Intertherm P3RA-048K Air Conditioner
Jan 02, 2011 | Intertherm P3RA-048K Air Conditioner
Dec 03, 2010 | Intertherm P3RA-060K Air Conditioner
Jun 22, 2008 | Intertherm Heating & Cooling
574 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: