Question about Reddy Heater RLP100 Portable Forced Air Propane Heater with Variable Heat Ouput
Runs longer with cover off.has run fine for 5 years this year i run diesel thru it about 2 months and has fine until now
First CARBON MONOXIDE WILL KILL YOU
#2 fuel is too dirty, use #1 or clear K-1.
I have found when running mine in any confined space like a garage, it will consume too much oxygen if not vented. It might run till it draws down the oxygen level. You start at 21% and draw down the oxygen to 14% that is where mine kicks out.
Clean out the filter, flush the tank, put in clean K-1, You might need to replace the igniter. Check your fuel line pressue (mine was 4 psi).
Posted on Jan 25, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 10, 2011 | Reddy Heater 60,000 BTU Kerosene...
Jan 20, 2010 | All-Pro Kerosene Garage Shop Heaters - All...
Jan 13, 2010 | Reddy HEATER R115 115,000-BTU PORTABLE...
Dec 29, 2009 | All-Pro Forced Air Kerosene Space Heater...
Dec 23, 2009 | Reddy Heater 60,000 BTU Kerosene...
Feb 05, 2009 | Reddy Heater-170,000 BTU Kerosene Deluxe
Jan 15, 2009 | Reddy HEATER R115 115,000-BTU PORTABLE...
Dec 18, 2008 | All-Pro Kerosene Garage Shop Heaters - All...
Aug 02, 2013 | Reddy Heater RLP100 Portable Forced Air...
120 people viewed this question
Usually answered in minutes!